Thermal shock is a situation where the water in aboileris suddenly displaced by water with substantially different temperatures. It causes rapid expansion or contraction of tubes, boiler plate, pipes, valves and fittings and is not good for the boiler or piping system. The end result will be leaking tubes, cracked pressure vessels, cracked cast iron sections, and a host of other problems.
Avoiding Thermal Shock
To prevent problems, large industrial boilers are not household boilers that typically do start and stop the circulating pump. Primary-secondary systems are suggested when possible.
If the pump needs to be cycled, we suggest temperature sensors and control strategies to prevent it from sending water at drastically different temperature to the boiler.
Slow start up can be done with small start up pumps, ramp up control or very slow control valves. Start the pump before the boiler, running the pump for some time after the boiler is shut off and always having flow when the unit is running.
Use blend pumps to temper the return water when needed.
Watch out for control or isolation valves, they need to be slow opening.
The boiler should be hold in low fire for gradual warm up and use relays to force it to low fire before shutdown.
Avoiding Thermal Shock is a crucial topic for anyone running hot water boilers.Contact usfor technical support.
Pre: How many boilers are needed
Next: Shutting down your boilers for the season
Contact us now if you have any question about our company and products [email protected]. Any of your inquiry and suggestion will be highly appreciated. We will keep your information completely private.
WANT TO FIND A BOILER FOR YOUR COMPANY ?CONTACT US